Scaling Your SCADA Architecture for Distribution Automation with sensors
How will you best deploy and scale your DA system?
Will you continue using the more traditional technique of installing Remote Terminal Units (RTUs) out in the field that is typical in today’s Supervisory Control and Data Acquisition (SCADA) deployments at substations?
Or, does your architecture need to mirror that of an Advanced Metering Infrastructure (AMI) system?
What is the best approach to future proof your automation build and investment?
In this whitepaper, we weigh the pros and cons of the three most popular DA architectures that have adopted the industry standard DNP3 protocol.
Download the whitepaper now!
By filling out this form and submitting your information, you consent to receiving updates from our team via our mailing list. You may withdraw consent at any time by utilizing the unsubscribe function at the bottom of our e-mail communications